19 Apr 21
I had an unsatisfactory EICR report with the following issues: 1 Inadequate degree of ingress (IP rating) for the external influences likely to occur in the location (522.3.1) bathroom light -C2 2 Bathroom trunking for mirror needs securing and junction box C2 3 Lighting circuit on B16 should B6 C2 4 Absence of RCD (411.4.9; 411.5.2;531.2) C2 5 No supplementary bonding where required C2 6 Continuity of conductors (643.2) ring main R1 and R2 F1 7 No main protective bonding noted to water within 600mm of service (543.3.2) can t locate stop tap washing machine and fridges in the way F1 8 Absence of warning notices C3
10 Apr 21
Need an Electrian Appliance installer to supply and fit both bathroom extractor and kitchen hood/extractor. Need a tradesman to remove the old extractor fan in the bathroom and replace with new one as the current one has suddenly stopped working. Please note: The fan in being connected with the bathroom light. Once the switch is activated from outside the bathroom, both the extractor fan and the light will be on together.
27 Jun 20
Some electric sockets need mending - loose, need a new light fitting on landing, couple of dimmer switches need changing and would like an electric socket putting nearer the washing machine. Also would like to discuss a quote to change a couple of fuse boxes - two are old fuse wire ones whereas the other two are trip switches.
21 Jun 19
1) Electrical wall switch plate ( white plastic one) with fused connection that is" Hot" to touch after 30-40 mins ON switch for the Electric unvented water heater 2)Have a humming noise upon switch on the water heater around 20 mins later. 3)The noise does stop upon switch off the water heater. I don’t know if the hot switch plate is related to noise of electric water heater.